Crawlspace and plumbing inspection! Do you need our home inspection services? Contact us at: 469-286-7093
New construction inspection: the driveway was sloped towards the house. this condition can promote rain water seepage through the brick wall weep holes as water levels increase.
Today's last home inspection of the day proves once again the importance of having your home inspected prior to purchasing. As it shows in this video a new plumbing system installed in this home where the bathtub drain was not properly connected and the water was draining under the slab foundation.
Do you need a home inspection? Please contact us at: At Home Safe Inspections 469-286-7093
Roof inspection: here is an example to why it is important to have your roof inspected prior to purchasing your house. during the inspection we found that the wrong type of fasteners had been used to install the shingles, some were loose and lift easily.
The importance of having your HVAC system service: Damage to the roof material and exterior wall siding was observed due to a clogged evaporator primary condensation line.
Inspecting a house crawlspace and plumbing system. Client complained of strong odors within the house but could not figure out why, because no leaks were visible around the toilets base. Upon further investigation we found that the plumbing system main vent stack pipe had completely collapsed to the ground and sewer gases were being release into the crawlspace and odors had found its way inside the house.
Attic access pull down staircase collapsed during inspection: here is a great example to why it is important to hire a qualified contractor for all jobs.
( potential fatal injuries to my clients were avoided )